Furnace flue must not have horizontal segments longer than 1 m. When passing Chimney through walls, ceilings or roofs should be used through-connections are made in accordance with the rules of fire safety. Safe installation of chimney flue should eliminate contact channels with electrical wiring, gas pipelines and other utilities. To clean the chimney at its base should provide a removable part (a glass) or a hole with a door. When an internal installation option vertical sections of the chimney of metal pipes are indoors. Flue pipes (tubes) are placed in internal walls and partitions. Outputs the chimney through the roof and floor decks with Special walk-through pipe.
When you install the chimney inside the mines is necessary to provide the door, enabling easy access to the inspection hole. If an inspection hatch located near impossible glass, allowed the extension of the chimney to the inspection hole. As a tip the chimney in mining performance should apply fairing mouth. For external installation option, vertical sections of chimney placed outside the building with a side terminal through the wall, subject to the warming of the outer pipe section to prevent condensation of moisture from the discharged products of combustion. The chimney is attached to special brackets wall. Flue pipes (tubes) that are usually placed at the internal walls and partitions of incombustible materials. The vertical sections of the chimney of metal pipes are placed outside the building to the side of the through the wall, provided the outer insulation of the pipe portion.